Cable is installed using a system incorporating eyebolts and turnbuckles attached to “L” braces or walls to carry the FabriDuct™ across the space horizontally. For lengths over 50 feet, vertical support cabling should be installed and attached to the horizontal cable every 25 feet to keep the system level.
Single cable is appropriate for FabriDuct™ diameters up to 24 inches. Double cable is highly recommended for applications where the FabriDuct™ diameter is 24 inches or larger.
FabriDuct™ can be hung from the track using either of two methods. The FabriDuct™ can be constructed with a cord-in feature which slides into the track providing a continuous connection, or by using a series of clips positioned every two feet along the FabriDuct™
Option 1: Flush Mounted to Ceiling
Track Flush Mounted to Ceiling
Option 2: Hanging with ClipsTrack with Hanger Supports
Single track is appropriate for FabriDuct™ diameters up to 24 inches. Double track is highly recommended for applications where the FabriDuct™ diameter is 24 inches or larger.